Last Friday, the equipment in the computer room was maintained regularly. During the maintenance, the personnel of the engineering company shut down the refrigeration system, and the personnel did not start the system after leaving the site. During the rotation rest / operation of the refrigeration equipment, some equipment did not start and could not work normally, resulting in the high temperature of some cabinets in the computer room from 8:32 to 9:15 on February 28. The air-conditioning system was restored at 9:20. Some servers need to be protected or suspended from death and need to be restarted to resume.
At noon, we have manually turned on all servers with normal order status but power off. Sorry for the inconvenience!
Sunday, February 28, 2021